1. Duplex Service DropConstruction
Application:To supply 120 volt aerial service for temporary service at construction sites,outdoor or street lighting . For service at 600 volts or lower at a conductor temperature of 75°C maximum.
2. Triplex Service Drop
Application: To supply power from the utility's lines to the consumer's weatherhead. For service at 600 volt or less (phase to phase) at a conductor temperature of 75°C maximum for polyethylene insulation 90°C maximum for crosslinked insulation.
3 Quadruplex Service Drop.
Used to supply 3 phase power, usually from a polemounted transformer, to the user's service head where connection to the service entrance cable is made. To be used at voltages of 600 volts or less phase to phase and at conductor temperatures not to exceed 75°C for polyethylene insulation 90°C maximum for crosslinked polyethylene(XLPE) insulated conductors.
Phase Conductor construction:The phase conductor is aluminum alloy 1350-H19 hard-drawn, compressed concentric-lay-stranded.
Neutral Conductor Construction
Cable assemblies are available with the following neutral conductors:
Aluminum conductors, coated-steel reinforced (ACSR), concentric-lay-stranded
Aluminum alloy 1350-H19 hard-drawn, concentric-lay-stranded
Aluminum alloy 6201-T81, concentric-lay-stranded
The standard insulation on the phase conductor is black low-density crosslinked polyethylene (XLPE)
Alternatively, black linear low-density polyethylene (LLDPE) insulation with a 75°C temperature rating is available upon request. Inspection Items:
1. B-230 Aluminum Wire, 1350-H19 for Electrical Purposes.
2. B-231 Aluminum Conductors, Concentric-Lay-Stranded.
3. B-232 Aluminum Conductors, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR).
4. B-399 Concentric-Lay_Stranded 6201-T81 Aluminum Alloy Conductors.
5. B498 Zinc-Coated Steel Core Wire for Aluminum Conductors, Steel Reinforced (ACSR).
6. Duplex Service Drop cable meets or exceeds all applicable requirements of ANSI/ICEA S-76-474
|Product Name||Service drop high/medium/low voltage 1000v aluminum conductor pvc insulation abc cable electrical AAC / ABC cable|
|Conductor||Copper / Aluminum, based on client's requirements|
|Construction||Bare copper wire|
|Color||Assorted upon request|
|Application||These cables are used for aerial cable transmitting power on long spans or under very server mechanical conditions.|
|Specification||CCC ISO certificated|
|Strict QC |
|Prompt delivery |
Rated voltage: 0.6/1kV, 1.8/3kV, 6/10kV, 8.7/10kV, 8.7/15kV, 12/20kV, 21/35kV, 26/35kV
Maximum Conductor Temperature: under normal (90°C), emergency (130°C) or short circuit no more than 5 s (250°C) conditions.
Min. Ambient Temp. 0°C, after installation and only when cable is in a fixed position
Min. Bending Radius: 20 x cable O.D for single-core non-armoured cables
15 x cable O.D for single-core armoured cables
15 x cable O.D for multi-core non-armoured cables
12 x cable O.D for multi-core armoured cables
Conductor:Tinned Copper, according to the VDE 0295/IEC 60228, Class 5.
Insulation: Polyolefin copolymer electron-beam cross-linked.
Outer Sheath: Polyolefin copolymer electron-beam cross-linked.
Sheath Color: Black/Red/Blue or as per customer's request.
Nominal Voltage:U0/U=600/1000V AC, 1000/1800V DC ;
Temperature Rating:-45ºC upto+125ºC, -40ºF upto+257ºF, Ambient temperature:25years(TUV) -40ºC upto +90ºC, -40ºF upto +194ºF.
Max.Short circuit temperature:280ºC, +536ºF.
Bending Radius:Fixed installation>4X Occasionally moved>5X
3.Low fire load:DIN51900
4.Approvals:TUV2PfG 1169/08.2007 PV1-F.
5. Application Standards:UNE211 23;UNE20.460-5-52, UTE C 32-502.
2.IP67 MC4 Connector
6.Flexible Power Cable 0.6/1kv
7.CE Sheathed Cable
8.UL&CE Standard Wire