2. Operating Features: 1)The maximum conductor operating temperature: 90°C During short circuit (lasting less than 5 seconds) the maximum temperature of the cable conductor shall not be above 250°C Environment temperature should be no lower than 0°C for laying the cable. 2)Bending Radius of the Cable: Single Core Cable: Non Armored Cable 20D, Armored Cable 15D Cores Cable: Non Armored Cable 15D, Armored Cable 12D. Remarks: D means practical external diameter of the cable
3. Model and Name
XLPE insulation PVC sheath power cable (Cu/XLPE/PVC)
To be laid indoors, in tunnel, cable furrow or pipe, the cable couldn't bear mechanical force outside
XLPE insulation PE sheath power cable (Cu/XLPE/PE)
XLPE insulation, steel tape armor, PVC sheath power cable
To be laid underground, the cable could bear certain mechanical force, but it couldn't bear great pulling force.
XLPE insulation, steel tape armor, PE sheath power cable
XLPE insulation, no magnetism steel tape armor, PE sheath power cable
XLPE insulation, thin steel-wire armor, PVC sheath power cable
Be applicable to the well, water inside and fall in the bad soil, the cable cans bear the equal dint outside the machine with pull the dint
XLPE insulation, have no the magnetism thick steel-wire armor, PVC sheath power cable
XLPE insulation, thick steel-wire armor, PVC sheath power cable
Be applicable to the well, underwater with the bottom of sea, the cable cans bear the bigger pressure with lead to pull the dint.
Our company-Shandong New Luxing Cable Co.,Ltd establish in the year of 1999 , so until now we have been in this line for more than 18 years .at present ,we have 150 empoyees in total , and annual sales volume is about 8 billion .our headquarter in Jinan City , the capital in shandong province . and our factory located in Dezhou City , Covering an area of more than 60 acres .
Strict Quality Test ( Raw Material & Finished Cable )