Single Core Two Core Three Core Four Core Five Core
25mm2, 35mm2, 50mm2, 70mm2, 95mm2, 120mm2, 150mm2, 185mm2, 240mm2, 300mm2, 400mm2, 500mm2, 630mm2.
N2XSY, N2XSEY, NA2XSY, NA2XSEY, N2XSRY, NA2XSRY, N2XSEBY, N2XSEYBY, NA2XSEBY, N2XSERY, NA2XSERY, N2XSEYRGbY, NA2XSEYRGbY, N2XS(F)2Y, NA 2XS(F)2Y, N2XS(FL)2Y, N2XSH, N2XSYRY
YJV, YJLV, YJSV, YJLSV, YJV72, YJLV72, YJSV72, YJLSV72, YJV22, YJLV22, YJSV22, YJLSV22, YJV32, YJLV32, YJSV32, YJLSV32
For power networks, underground, outdoors and in cable ducting. It is recommended that the installation instructions indicated by the Local Electric Code, or any equivalent, be followed, so that the safeguarding of persons and the integrity of the product will not be affected during installation.
Stranded round compacted copper or aluminum conductor (Cu / Al ), copper wire annealed.
XLPE (Cross-Linked Polyethylene)
Copper tape screen or copper wire screen (CTS / CWS )
PVC (Polyvinyl Chloride)
Single Core: Aluminium Wire Armoured (AWA) Multi-core: Steel Wire Armoured (SWA) or Steel Tape Armoured (STA)
PVC (Polyvinyl Chloride), flame retardant PVC, PE, LSOH, HFFR
Red or Black
0°C to 90°C
Minimum Bending Radius:
Single Core: 15 x overall diameter Three Core: 12 x overall diameter (Single Core 12 x overall diameter and 3 core 10 x overall diameter where bands are positioned adjacent to joint or terminations provided that the bending is carefully controlled by the use of a former)