1.XLPE Power Cable Suitable for 15kw Generator
2.Nyy Nayy-J -O PVC PVC 0.6/1kv Direct Burial Underground Cable
3.CU/XLPE/PVC Copper Insulated MV Underground Power Cable for 33/11kV Substation
4.medium voltage power cable
ITEM NAME : XLPE power cable Suitable for 15kw generator
1,3*10+1*6 Power Cable 2,Suitable for Generator 15kw 3,IEC 60502-1997 Standard 4,Competitive Price and High Quality
Electirc / PVC Cable with XLPE Insulated Product Description CU (AL)/XLPE Insulated power cable Copper (Aluminum)/XLPE insulation/Steel wire armour/PVC Sheath cables
Spec. of Power Cable
The conductors shall be either of Class 1 or Class 2 of plain or metal-coated annealed copper or of plain aluminium or aluminium alloy, or of Class 5 of plain or metal-coated copper in accordance with IEC 60228.
XLPE material and thickness shall be as per IEC 60502 or BS 5467 rated for 90C continuous operation.
3. Inner covering
The inner coverings may be extruded or lapped. For cables with circular cores, except cables with more than five cores, a lapped inner covering shall be permitted only if the interstices between the cores are substantially filled. A suitable binder is permitted before application of an extruded inner covering. The material is compatible with the insulating material,The materials used for inner coverings and fillers shall be suitable for the operating temperature of the cable and compatible with the insulating material.For halogen free cables, the inner covering and fillers shall also be halogen free compound.
Aluminum/galvanized steel/steel wires applied helically over the Inner Covering as per IEC 60502-1, or double aluminum/steel tapes and copper/tinned copper wire can also be manufactured upon request.
5. Outer Sheath
Outer sheath shall be of extruded PVC Type ST1/ST2 as per IEC 60502-1, Polyethylene type ST3/ST7, Halogen free compound ST8, Polychloroprene, chlorosulfonated polyethylene or similar polymers, type SE1 are also available on request.
6. Fire Performance of Cable Sheaths
Cables can be supplied with special flame retardant PVC outer sheath to comply with the flame test requirements of IEC 60332-3-22, IEC 60332-3-23 and IEC 60332-3-24, Halogen Free material comply to IEC60754-1/2 and IEC 60684-2.