National Standard GB/T
Insulation level and withstand voltage rating of the cable
Combustion test and Mechanical test
Flame spread test
Smoke divergence test
Circuit integrity test
Halogen content test
Electrical cable system combustion test
Fire extinguishing system:
Shopping mall, department store, hospital, school, stadium, exhibition center, train station, airport, subway, commercial buildings, hotels, places with dense population, iron and steel enterprises, High building..
High temperature places, such as Steel,glass workshop,
Flammable and explosive places,such as petrochemical,chemical,hospital,Nuclear power and water industry enterprise.
Ships and warships
A:950-1000ºC fire resistance
V:PVC outer sheath
4.Test Method for Fire resistance:
Pass three requirements of BS6587 Fire resistance test
1)Under 950ºC flame continuous to power 180mins without breakdown.
2)Under 650ºC flame for 150mins and water spray for 15Mins without breakdown
3)Knock and shock under 650ºC flame without breakdown.
High temperature and fire resistance,In case of load 1000V bear 950ºC burning for 3 hours.
With Character of anti-spray and anti-mechanical impact
Continous length can reach 1000M
Short production time
High rated voltage can reach 0.6/1KV
Low power lost and high current carrying
Energy saving and enviorment protection
Radiation protection,long life,Safe and reliable
Cross sectional area mm2
Strand copper conductor Mineral insulation mineral fire isolation LSZH Sheath